ПвВГЭнг(А)-FRLS – (PvVGEng(A)-FRLS) – Russian analogue of NHXCYu Fire Resistance Low Smoke FE180 MICA
SCOPE AND PURPOSE
The cables are designed for transmission and distribution of electric energy in stationary electric installations, for installation in cable structures, buildings and underground structures, including flammable and explosive areas, for supply chains of the equipment, which operates in fire.
The cables of types PvPGEng(A)-FRLS and PvBPng(A)- FRLS of rated voltage 3 kV are used in DC voltage units and they are available in single-core modification.
The class of fire hazard of the cables according to GOST 31565-2012 П1б.188.8.131.52.
Nominal voltage, kV – 0.66, 1 or 3
Ambient temperature during cable operation, 0C - from -50 to +50
Resistant with a relative humidity up to 98% at ambient temperature, degree Celsius, up to +35
Minimum bending radius, diameters of cable:
for single-wire – 10
for multi-wire – 7.5
Service life, years, not less: 30
Flame retardant at group installation in bunches on category: А
Equivalent toxicity index, g/m3 , more than: 40
Fire resistance of the cable, minutes, not less than: 180
Copper, single-wire or multi-wire of the 1st or 2nd classes according to GOST 22483-2012, of the cross-section for 0.66 kV – 1.5 – 50 mm2 ;
for 1 kV – 1.5 – 240 mm2, single-wire – 50-630 мм2;
for 3 kV – 240 – 360 mm2.
The lapping with mica tapes.
Cross-linked, halogen free, polymer composition.
Screen for single-wire cables of nominal voltage 3kV:
It is made of copper tapes or copper wires and a copper tape overlaid spirally.
Insulated conductors of multi-core cables on 0.66 and 1kV are twisted in a cable core.
The cables have got distinctive markings of insulated cores: color or digital.
Inner sheath or separating layer (for armored cables on voltage 3kV)
It is made by extrusion with filling with the halogen free polymer compositions.
For cables of types PvBShvng(A)-FRLS is laid helically with two steel, galvanized tapes.
It is possible to lay the PET-tapes by winding or longitudinally over the armor.
Cable sheath or jacket
PVC-compound of low fire hazard.
|Number and nominal cross-section of conductors (mm2)||External diameter of cable, mm||Weight, kg|