РВГ-Пнг(А)-FRLS (RVG-Рng(A)-FRLS) - Russian analogue of NHXIFMY Fire Resistance Low Smoke FE180/E30 KERAM
SCOPE AND PURPOSE
The cables are designed for transmission and distribution of electric power in stationary installations on the nominal alternating voltage to 0.66 and 1kV and frequency 50 Hz. The cables do not spread combustion at group stationary installation of cable lines, in the absence of mechanical effects and keep working when exposed to flame not less than 180 minutes.
They are designed for wiring and networks of the wiring circuits of emergency power supply of the equipment (current collectors), in residential and public buildings, in the surgical departments of hospitals, in office premises, equipped with computer and microprocessor devices, entertainment complexes and sports facilities, as well as at other objects with the high demand of fire safety.
The class of fire hazard of the cables according to GOST 31565 for cables П1б.188.8.131.52.
Number of conductors
2 or 3.
Copper, of circular form, single-wire core, with the cross-section from 1.5 to 16mm2 or multiwire core with the cross-section from 10 to 16mm2
Core arrangement and twisting
For RVG-Рng(A)-FRLS insulated cores situated in parallel in one flat.
PVC-compound of low fire hazard.
|Number of conductors, nominal cross-section (mm2), construction, voltage (kV)||Calculated diameter of cable, mm||Calculated weight of cable, kg/km|