КПСВЭЭВнг(А)-LS (KPSVЕEVng(A)-LS) - Russian analogue of J-Y(St)Y(St)-Bd Flame Retardant Low Smoke
SCOPE AND PURPOSE
The cables are designed for installation of fire and security alarm systems, systems of access control and other management systems, control and communications in the conditions of stationary laying inside of buildings and structures if it is necessary to protect the electric circuits from the influence of external electric fields.
The class of fire hazard of the cables according to GOST 31565 П1б.184.108.40.206
Copper, single-wire of the 1 class according to GOST 22483, with the cross-sections from 0.2 to 2.5 mm2.
PVC-compound of low fire hazard (color-coded conductors).
Core arrangement and twisting
Insulated conductors are twisted in a pair.
Alum polymer tape with a contact conductor of copper, galvanized wire is lapped in the way of winding or longitudinally by overlapping over each pair individually in two-pair cables
PVC-compound of low fire hazard.
|Number of pairs in cable, pcs||Cross-section, mm2||External dimensions or diameter of cable, mm||Calculated weight of 1km of cable, kg/km|